LED BATTENS HFB T8 G13 BASE
- Suitable for HLL T8 G13 base LED lamps
- LED drivers included for HLL T8 LED lamps
- With optional reflectors and diffusers
- Various choices for different series of LED lamps
- Available in single and double lamp versions
- Batteries with 2 or 3 hours options
|Body||White powered coated sheet body|
|Lamp holder||BJB, flame retardant grade|
|Wires||UL approved, 105°C|
|Terminal block||BJB, flame retardant grade|
The driver is AC and DC LED drivers built into one single unit.
With the internal micro-processor, the whole system is software controlled. These include battery charging, discharge discharging, system changeover, fault protections, LED indications and infrared remote control.
The improves system reliability and makes the system smarter for the whole operations.
The drivers also have buit-in active power factor correction with very low harmonic distortion. Protections with over-current, short-ciruict and open-circuit are provided with automatic restart for ease of use.
Five steps dimming is provided via the infrared remote controller.
EN 61347-2-1 Lamp controlgear. Particular requirements for starting devices (other than glow starters)
EN 61347-2-13 Lamp controlgear. Particular requirements for d.c. or a.c. supplied electronic controlgear for LED modules
EN 62384 DC or AC supplied electronic control gear for LED modules. Performance requirements
EN 60598-1 Luminaires. General requirements and tests
EN 60598-2-22 Luminaires. Particular requirements. Luminaires for emergency lighting
EN 55015 Limits and methods of measurement of radio disturbance characteristics of electrical lighting and similar equipment
EN 61000-3-2 Electromagnetic compatibility (EMC). Limits. Limits for harmonic current emissions (equipment input current ≤ 16 A per phase)
EN 61000-3-3 Electromagnetic compatibility (EMC). Limits. Limitation of voltage changes, voltage fluctuations and flicker in public low-voltage supply systems, for equipment with rated current ≤ 16 A per phase and not subject to conditional connection
EN 61547 Equipment for general lighting purposes. EMC immunity requirements
FSD Circular Letter No. 1/2006: PPA-104(A) 4th Rev Fire Safety Standards for Emergency Lighting
|HFB#-12L%||T8 G13 600mm||1||610|
|HFB#-13L%||T8 G13 900mm||1||912|
|HFB#-14L%||T8 G13 1200mm||1||1220|
|HFB#-15L%||T8 G13 1500mm||1||1525|
|HFB#-22L%||T8 G13 600mm||2||610|
|HFB#-23L%||T8 G13 900mm||2||915|
|HFB#-24L%||T8 G13 1200mm||2||1220|
|HFB#-25L%||T8 G13 1500mm||2||1525|
※ Omit “#” for standard, replace with “R” for adding reflectors, replace with “D” for adding diffusers
※ Replace “%” with “E2” or “E3” for 2-hr or 3-hr emergency lighting option
※ Add suffix “F” for optional fused terminal blocks